Aerating ground water
Northern Thailand government water supply facility. Helping with a refurb they identified as an iron oxide problem. In fact, it was calcium carbonate clogging the pipes stained brown from the modest levels of iron in the water. It was cheaper to replace the pipes rather than clean them. An interesting aeration setup too.